360 Degree Ceiling Mount PIR Presence Sensor / Occupancy Sensor -Dual Channel for HVAC and Lighting Control (DIM) - Conference Room
||Reach: 8 - 20 mts. adjustable in a square detection pattern to eliminate any blind or undetected areas. The fine / small motion area is 8x8 mts. (64 sq.-mts.)
|Mechanically Adjustable Reach
||The square detection zone can be mechanically adjusted with a potentiometer for specific detection in the area.
|Technical Highlights||The sensor has 2 channels, one for the 1-10V DIM analog interface by means of a constant lighting controller. The second channel operates the heating, ventilation and air conditioning systems in relation to presence only.|
|Lighting Controller||A pre-selected brightness level can be maintained. This function allows the lighting level at 10% after the stay 'ON' time elapses when no movement is detected. This feature can also be interfaced with the ambient lux level.|
|Applications|| Conference rooms, Training Halls and Meeting rooms, Office Cabins, Classrooms, Staff Rooms
|Technology||Passive Infrared / PIR - 4800 switching zones and 13 detection levels for sensing small movements normally found in a seated postion, with 4 highly sensitive pyro detectors. The digital technology improves signal evaluation without switching errors.|
||Ceiling Mount PIR Presence Sensor - Mounting Height: 2.5 mts to 10 mts.|
||Lighting Channel : 1000 W uncorrected inductive loads like t5 lights, CFL, fluorescent lamps/tubes with electronic ballasts
Controlled Output : 1-10 V, 50 electronic ballast max. (100 mA max.)
HVAC Channel : 1A max. for connection to a relay or contactor to switch HVAC loads.
Output No. 1
|:: 30 sec. - 30 minutes
:: Automatic time adjustment - The sensor analyzes the movement and automatically adjusts the time delay for the user.
:: Basic Brightness : 0 - 30 minutes for 10% basic brightness level. This time setting can maintain lux level of the lamp when no movement is detected. As soon as a person is present the light intensity is increased to the pre-selected brightness level.
Output No. 2
|:: 1 minutes. - 2 hours - Manually adjustable - switch 'ON' delay
:: 0 sec. - 10 minutes, Automatic time adjustment - switch 'OFF' delay. The room surveillance function allows the user to set a delay time before starting the HVAC loads. This feature automatically adjusts the time for the starter based on the movement pattern
|Lux setting facility
||Lux level with Twilight setting can be done through a hand-held remote control. There are 6 typical room situations to choose from. Constant light control with mixed light measurement|
|Master & Slave||Individual luminaires can be hardwired for connecting them in parallel which is suitable for the Master & Slave Operation and enhancement of the zonal coverage of detection.
|Handheld Remote Control
||Infra Red Control available for parameter settings|
||230V AC 50Hz|
|IP Rating||IP 54 with surface mounting and IP 20 with recessed mounting.|
Clamping-type ceiling adapter Control PRO UP BoxSurface-mounting adapter
Control PRO AP Box (IP 54)
How We Work
Sensor Planning : Know More
Potential Savings Prediction : Know More
Site Survey : Know More
Energy Saving Calculator : Know More
*Are Mandatory fields